SZ series single stage water ring vacuum pump
Model No.: BODA-185
Product Name: S Series Double Suction Pump
Packaging: wooden box
Place of Origin: china
Supply Ability: 500
HS Code: 4101201190
SZ water ring vacuum pumps are available in four sizes: SZ-1, SZ-2, SZ-3 and SZ-4. The large vacuum generated by the pump is between 86 and 95%. The large pressure that can be formed by SZ-1 and SZ-2 is 1.0~1.4 kg/cm2. The large pressure of SZ-3 and SZ-4 under the power of the motor is 1.5 kg/cm2, if the motor power is increased. , the large pressure is 2.1 kg / cm 2
Use and specifications of SZ type water ring vacuum pump
SZ water ring vacuum pumps and compressors are used to pump or compress air and other non-corrosive, water-insoluble gases to create vacuum and pressure in a closed container.
SZ water ring vacuum pumps are available in four sizes: SZ-1, SZ-2, SZ-3 and SZ-4. The large vacuum generated by the pump is between 86 and 95%. The large pressure that can be formed by SZ-1 and SZ-2 is 1.0~1.4 kg/cm2. The large pressure of SZ-3 and SZ-4 under the power of the motor is 1.5 kg/cm2, if the motor power is increased. , the large pressure is 2.1 kg / cm 2 (pump type meaning: such as SZ-1, S-water ring type, Z-vacuum pump, 1- pump serial number)
Working principle of SZ type water ring vacuum pump
The SZ water ring vacuum pump is shown in Fig. 1. The impeller 1 is eccentrically mounted in the pump body 2, and a certain height of water is injected into the pump during starting, so when the blade wheel rotates, the water is subjected to centrifugal force on the pump body wall. Forming and rotating the water ring 3, the upper inner surface of the water ring is tangent to the hub and rotates along the main direction of the arrow. During the first half turn, the inner surface of the water ring is gradually separated from the hub, and the SZ water ring vacuum pump is thus between the impeller blades. Forming space and gradually expanding, so that air is sucked in the suction port; during the second half turn, the inner surface of the water ring gradually approaches the hub, and the space volume between the blades decreases, and the air between the blades is compressed. discharge. When the impeller rotates once a week, the volume of space between the blades changes once, and the water between each blade reciprocates as if it were a piston. The SZ water ring vacuum pump continuously draws gas. Since water will heat up during work and some of the water will be drained together with the gas, the SZ water ring vacuum pump must be constantly supplied with cold water to cool and replenish the water consumed in the pump during operation. The supplied cold water is preferably 15 °C.
When the gas discharged from the SZ water ring vacuum pump is exhaust gas, a water tank is connected to one end of the exhaust gas, and after the exhaust gas and a part of the water discharged into the water tank, the gas runs away from the outlet pipe of the water tank, and the water falls into the water tank. The bottom is returned to the pump through the return pipe. If the cycle time is long, it will heat up. At this time, a certain amount of cold water should be supplied from the water supply of the water tank.